In recent years, the ventilation pipe plays a very important role in our daily life. With the continuous expansion of its application scope, more and more people choose to install it. Do you know what the installation layout points are? Next, Shandong ventilation pipe installation and processing factory takes you to the following to understand.
1. When there are many pollution sources, they can be concentrated in one purification system, or they can be divided into several systems. However, the mixture of pollutants will cause combustion, explosion danger, gases with different temperatures and humidity. After mixing, condensation, dust or gas properties in the pipeline will appear, which will affect the recovery or purification efficiency.
2. The layout of ventilation pipe processing system should reduce the resistance.
3. The laying principle of the ventilation pipe installation system is that the pipe laying should be clear and concealed, and the open installation is generally adopted, because the open installation is convenient for maintenance. When the open installation cannot be adopted, the concealed installation method should be considered, and the pipes should be concentrated as far as possible
Parallel laying along the wall or column as far as possible, if the pipe diameter is large or insulation should be arranged near the wall side. Generally, when two pipes are arranged in parallel, the spacing shall not be less than 100-200 mm.
Shandong ventilation pipeline
4. In the layout of pipeline processing system, small leakage of the whole system should be ensured, and sufficient air volume should be ensured at the suction port.
5. The connection principle of the pipeline processing system is that in the pipeline with welding as the main connection method, a sufficient number of flange connections should be set, and in the pipeline with thread as the main connection method, a sufficient number of movable joints should be set, so as to be cheap for installation, disassembly and maintenance.
6. The support principle of the ventilation pipe processing system is that the pipe should not be directly supported on the equipment with the valve, and the support or hanger should be set separately. The welding position of the pipe should be at the place where the construction is convenient or the stress is small, and the welding seam should not be at the support and the distance should not be less than 200 mm.
7. The layout of the system network, in order to facilitate the management and operation adjustment of the pipe network, the pipe network system should not be too large. When there are multiple branch pipes in the same system, these branch pipes should be controlled step by step, and the suction points of the same system should not be too many, and the pressure balance of each branch pipe must be paid attention to. There are three kinds of pipe network layout: main pipe, individual pipe and ring pipe.
In the process of pipeline installation, if the installation is not good, it will produce noise, air leakage, unreasonable layout, resulting in pipe waste and other problems. It is said that three parts of the product, seven parts of the installation, and the installation is more important than the product itself. It is recommended that you choose the installation team.