Jinan high temperature, high temperature smoke exhaust machine can be used in the kitchen of Jinan.
Jinan hotel kitchen smoke hood
(1) It should be set in the upper part of the high smoke exhaust outlet of the smoke exhaust system, and should be set in the machine room separated by partition wall with fire resistance limit of not less than 2.5h. The door of the machine room should be fireproof door with fire resistance limit not less than 0.6h.
(2) In order to facilitate maintenance, the distance between the shell of exhaust fan and the wall or equipment shall not be less than 60cm
(3) The connection between exhaust fan and exhaust flue should be reasonable. It has been proved that the performance of the fan is often decreased because of the incorrect connection between the exhaust fan and the exhaust duct.
(4) The smoke exhaust fan and smoke outlet shall be equipped with interlock device. When any smoke outlet is opened, the smoke exhaust fan can start automatically. That is to say, once the fire alarm is given and the smoke exhaust outlet is opened manually or remotely by the fire control room, the smoke exhaust fan will be put into operation immediately and the ventilation and air conditioning system in the fire area will be shut down immediately.
(5) The smoke exhaust fan shall be set on the concrete or steel frame foundation, but vibration damping device may not be set. There should be no regulating device on the suction pipe of the fan.
The above contents are sorted out according to the problems encountered in the actual work for reference. If there are any problems, please communicate and correct them in time. 上一篇：如何何应对排烟管道破损问题？